AP, Apr. 23, 2014: Board chairman Ted Wyka previewed the [Department of Energy's Accident Investigation Board report] findings at a community meeting Wednesday […] Shortcomings were found at almost every step, from a more than 10-hour response to the initial emergency alarm to a bypass in the filtration system that allowed the radiation to escape above ground. “The bottom line is they failed to believe initial indications of the release,” Wyka said. […] Crews are still working to identify the source of the leak, which sent low levels of radiation into the air around the plant, but officials believe it occurred in the area where toxic waste was last being handled. Officials Wednesday night said there were people working in that area at the time of the fire, but did not say what they were doing.
Wall St. Journal, Apr. 23, 2014: A separate problem surfaced during the Feb. 14 radiation accident: The containment system leaked, allowing some radiation to escape from underground. The plant hadn’t experienced a radiation accident previously, and site-maintenance procedures didn’t require that the containment system be tested for leakage, Energy Department officials said. […] While a radiation-containment system was installed, it didn’t have the “safety pedigree that we would want.” Such a radiation accident at the site “wasn’t supposed to happen for 10,000 years,” said Geoffrey Fettus, a senior attorney at environmental group Natural Resources Defense Council and a former New Mexico state assistant attorney general who worked on issues related to the plant.
Ted Wyka, chairman of Department of Energy’s Accident Investigation Board, Apr. 23, 2014 (at 1:04:00 in): HEPA filter bypass dampers, they represent a pathway — and they did — of unfiltered exhaust to the environment. […] They have an unacceptable design leakage for a containment boundary. That bypass dampers around the HEPA filters, which operated with the efficiency that you would expect… design leakage reduces the overall efficiency of the HEPA filter system, and was the source of the release on Feb. 14, that bypass around the HEPA filters.
Published: April 24th, 2014 at 9:17 am ET
- NRC: “Degraded condition” at Illinois nuclear plant — Leak inside primary containment — Days after emergency due to lightning strike April 30, 2013
- “Air detection teams deployed” after U.S. nuclear plant accident — “Evacuation signs were posted throughout community” — Concerns over building stability? — Worker: Worst thing to happen in 30+ years (VIDEOS) April 1, 2013
- Video: Giant sinkhole’s ‘containment system’ could encompass 70 acres January 31, 2013
- “WIPP release story doesn’t add up… accident is unbelievable” — New tests show “high level” release underground — “Contains things far more radioactive than High Level Waste” — “I want to hear what really happened down there” (VIDEO) March 6, 2014
- Expert: ‘Cracked’ nuclear container “blew top off” at WIPP — Hundreds more drums at dump risk ‘energetic reaction’ and radiation release — Insider: Get forklift and remove them before another accident — Official: No ‘imminent’ public threat ‘at this time’ (VIDEO) May 19, 2014